ANSI/ASME A13.1 is the most common pipe identification standard used in the United States. The standard specifies the primary and secondary means of identifying pipe contents, as well as, the size, color and placement of the identification device.
The legend (name of pipe content) and directional flow arrow remain the primary means of identifying pipe content. The size and placement of the marker arrow has not changed. See ANSI/ASME size chart (see below) and installation guide for details (see below).
From the official ASME A13.1-2015 guidelines on legend: "Positive identification of the contents of a piping system shall be by lettered legend, giving the name of the contents in full or abbreviated form. Arrows shall be used to indicate direction of flow. Where flow can be in both directions, arrows in both directions shall be displayed. Contents shall be identified by a legend with sufficient additional details such as temperature, pressure, etc. as are necessary to identify the hazard."
The secondary means of identification is the color code of the marker. In addition, the terminology of inherently hazardous or non hazardous has been removed from the standards. The combination of Yellow / Black is now assigned with flammable and oxidizng fluids, and Green / White shall now identify potable, cooling, boiler feed and other waters. This means that legends such as hot water, cold water and steam will now all use the color code of Green / White.
Since 2007, the other significant color changes included the addition of Brown / White for combustible fluids and Orange/Black for toxic or corrosive fluids. The fact that the standard has identified specific colors for flammable fluids, combustible fluids and toxic or corrosive fluids means you must consult Material Safety Data Sheets before selecting a color. Further, if the pipe content contains multiple hazards (flammable and toxic) it must be determined which poses the greater risk and marked accordingly. For example, if chilled or heating systems contain toxic treatments the color combination should be Orange / Black. The standard since 2007 also identifies for the first time four additional used identified color combinations and specifically identifies all of the exact background colors to be used. The exact colors are safety colors contained in the ANSI Z535.1-2007 standard.
From the official ASME A13.1-2015 guidelines on color: "Color should be used to identify the characteristic hazards of the contents. Color should be displayed on, or contiguous to, the piping by any physical means, but its use shall be in combination with the legend."
ANSI/ASME A13.1-1996 Colors:
ANSI/ASME A13.1-2015 Colors:
Definition of materials (from the official ASME A13.1-2015 guidelines):
Additionally, potable, cooling, boiler feed and other water includes hot water, cold water and steam.
Seton Pipe Marking Systems Meet the ASME(ANSI) A13.1-2015 Standard
Visibility Markers shall be located so that they are readily visible to plant personnel from the point of normal approach. Seton Pipe Markers instantly tell you all you need to know about pipe contents, direction of flow and whether hazardous or safe.
1. Obtain a legend list of all pipe contents in your plant.
2. Collect the following data on your piping systems. This may require tracing lines to determine quantities and sizes.
***Note: You may be able to use blueprints or P&IDs if they are current instead of walking down all of your lines. Seton also offers Take-Off Services of which we can determine your pipe marking requirements for you.
3. Select color of marker.
Seton Pipe Marking Systems Meet ASME (ANSI) Size Recommendations: The A13.1-2015 standard also makes recommendations as to the size of letter height and length of color field for various pipe diameters. These recommendations are shown in the table. Seton markers, used properly with arrows and banding tape or arrow tape, meet or exceed the standard.
Seton Pipe Marking Systems Meet ASME(ANSI) Color Recommendations: Unmarked pipes mean danger to both life and property. Numerous injuries have occurred through ignorance of pipe contents, particularly when outside agencies are called in under emergency conditions.
Over 150 stock legends available! Still can't find the wording you need? No problem, we can customize markers to your exact wording.